By Xiao Q. Chen (Original Publication: Feb. 25, 2015, Latest Edit: Mar. 23, 2015)
Sodium sulfur (NaS) batteries are a type of molten salt electrical energy storage device. Currently the third most installed type of energy storage system in the world with a total of 316 MW worldwide, there are an additional 606 MW (or 3636 MWh) worth of projects in planning. They are named for their constituents: Sodium (Na) and Sulfur (S).
Although the battery’s conceptual origins stem as early the World War II era as a way to power Germany’s V-2 rockets, significant research and development of the sodium sulfur battery for modern energy storage began only around two decades ago through a joint effort between Tokyo Electric Power Company and NGK Insulator, Ltd. ,  Currently, the battery’s performance is well tested and it enjoys notable recent commercial experience.
Figure 1. Battery Structure
The typical sodium sulfur battery consists of a negative molten sodium electrode and an also molten sulfur positive electrode. The two are separated by a layer of beta alumina ceramic electrolyte that primarily only allows sodium ions through. The charge and discharge process can be described by the chemical equation,
2Na + 4S ↔ Na2S4.
In the discharge process, the two elements combine to form sodium polysulfides but in the charging process, the sodium ion is released back through the electrolyte.  The discharge process produces roughly 2 Volts. 
Operation and Properties
Properties of the Sodium Sulfur Battery
|Capacity:||300MWh (renewable integration support)/7.2 MWh (grid&industry)|
|Power:||50MW (renewable integration support)/1MW (grid&industry)|
|Energy Density:||150-240 J/kg|
|Power Density:||15-230 W/kg|
|Charge/Discharge Duration:||6 hours (renewable integration support)/7.2 hours (grid&industry)|
|Response Time:||Quick (a few milliseconds)|
|Lifetime (years/cycles):||15 yrs/4500 cycles|
|Cost Per Capacity:||520-550 kWh (renewable integration support)/545-555 kWh (grid&industry)|
Due to requiring high temperatures to operate, uses for sodium sulfur batteries are limited to large, immobile technologies, such as distribution grid support. Other uses include, but are not limited to, wind power integration, and high-value applications on islands. The largest installation of sodium sulfur batteries powers a wind-stabilization project in Rokkasho, Japan.
Figure 2. Wind Farm in Rokkasho, Japan with NaS Battery Integration 
Usage of this battery type in space missions has been proposed in 1986 and1991 due to its high energy density and high charge/discharge rates. However, no official source can be found stating operational use of this battery outside of testing.
One advantage of a sodium sulfur battery is that it is a mature system with established experience and presence on the market. Since their container is entirely sealed while in operation, they are environmentally friendly. Their cost per capacity is in the middle compared to other options. Although they are not the most cost effective in terms of cost per capacity or output and duration, this type of battery does not require a supportive geographical location (such as an abundance or water and space or an underground cave) to remain in operation like pumped hydro systems and CAES systems. The battery also has no self-discharge, unlike lead-acid options, NiCd options, and Li-ion options. Their extremely quick response time make them an excellent candidate for responding to changes in demand in a grid system.
The battery type’s main disadvantage is that it requires a heat source for operational conditions. This makes the battery more or less immobile and impractical for residential use, especially when compared to the Li-ion rechargeable batteries currently employed on most mobile computing devices. The most unfortunate of all, is it also drains part of the battery’s efficiency since the heat source needed for continuing operation is maintained using part of the battery’s own stored energy.
 “Alternate Battery Systems.” Battery University. Accessed Feb, 24 2015 http://batteryuniversity.com/learn/article/alternate_battery_systems
 “Physical Sciences Division Research Highlights.” Pacific Northwest National Laboratory. May 2009. Accessed Feb, 24 2015. http://www.pnl.gov/science/highlights/highlight.asp?id=617
 Chen, H., Cong T.N., Yang, W., Tan, C., Li, Y., Ding, Y. “Progress in electrical energy storage system: A critical review” Progress in Natural Science Volume 19, Issue 3, 10 March 2009. Pages 291–312. ScienceDirect. doi:10.1016/j.pnsc.2008.07.014
 “Energy Storage for Power Systems Applications: A Regional Assessment for the Northwest Power Pool (NWPP).” Pacific Northwest National Laboratory. April 2010. Accessed Feb, 24 2015 http://www.pnl.gov/main/publications/external/technical_reports/PNNL-19300.pdf
 Steudal, R., Steudal Y. “Polysulfide Chemistry in Sodium-Sulfur Batteries and Related Systems- A Computational Study by G3X(MP2) and PCM Calculations.” Chemistry – A European Journal Volume 19, Issue 9, 16 January 2013. Pages 3162-3176. ResearchGate. doi: 10.1002/chem.201203397
 “Rokkasho-Futamata Wind Farm | Case Study” Clean Energy | Action Project. Accessed Mar, 23 2015http://www.cleanenergyactionproject.com/CleanEnergyActionProject/CS.Rokkasho-Futamata_Wind_Farm___Energy_Storage_Case_Study.html
 “Sodium-sulfur batteries for spacecraft energy storage” Harvard-Smithsonian Center for Astrophysics. Accessed Mar, 23 2015http://adsabs.harvard.edu/abs/1986batt.work…19D
 “19920013524.pdf” NASA Technical Reports Server. Accessed Mar, 23 2015 http://ntrs.nasa.gov/archive/nasa/casi.ntrs.nasa.gov/19920013524.pdf
 Divya, K.C., Østergaard J. “Battery energy storage technology for power systems—An overview.” Electric Power Systems Research Volume 79, Issue 4, April 2009. Pages 511-520. ResearchGate. doi: 10.1016/j.epsr.2008.09.017